Views: 1789 Author: Site Editor Publish Time: 2023-02-17 Origin: Site
Sifang now has advanced drum production lines, header production lines, membrane wall production lines and serpentine pipe production lines, including CNC four roll bending machines, CNC blanking, large porous CNC drilling machines, CNC bevel machines, plasma cutting machines, various welding machines, various machining machines, various types of pipe benders, large and medium-sized bending machines, heat treatment furnaces, large paint spraying rooms, 150t cranes As well as various metal nondestructive testing equipment, physical and chemical experiment special equipment and other test and detection equipment and instruments, it provides a complete hardware guarantee for the R&D and production of various products of the company.
1. Preparation before installation
(1) Check whether the accessories of the boiler dust collector equipment are complete, whether the main machine is damaged, and whether the connecting parts are safe and reliable. If there is any problem, contact the manufacturer to solve it before installation.
(2) The dust remover equipment is inseparable from the fan, so when installing the boiler bag dust remover, it is necessary to check whether the operation of the boiler bag dust remover fan is noisy or in bad condition. If so, it is necessary to debug the fan before use.
2. Formal installation
(1) The boiler dust remover is large and heavy, and should be placed on a flat and firm foundation. The equipment should contact the ground, and the ground should be hardened in advance.
(2) When installing the electrical control system of the boiler bag-type dust removal equipment, it is necessary to understand its basic working principle, and refer to the precautions in the operating instructions of the electrical control system when installing and debugging.
(3) The input end of the electromagnetic pulse valve of the boiler dust removal equipment is inserted into the metal pipe of the gas reservoir, and its output end is inserted into the spray pipe of the dust removal equipment. The two ends of the valve are equipped with rubber sealing rings and fixed nuts, so that the electromagnetic pulse valve can be reliably fixed and sealed.
(4) When installing the water separation filter pressure reducing valve of the boiler dust collector, the arrow direction of the water separation filter pressure reducing valve must be consistent with the flow direction of the compressed air, and the outlet pressure of the pressure reducing valve should be adjusted to 0.4~0.6MPa.
(5) If the dust removal equipment of the boiler is installed outdoors, it is necessary to install a rain cover or rain shed.
3. Commissioning after installation
After the installation of the boiler dust removal equipment, it is necessary to carry out commissioning. Turn the pulse knob, and the pulse injection controller sends instructions to open the electromagnetic pulse valve in order to observe whether the dust removal action of the boiler bag filter is correct.
The above is Jiangsu Sifang Clean Energy Equipment Manufacturing's answer to this question. If you have any questions about other boiler related issues, please consult Jiangsu Sifang Clean Energy Equipment Manufacturing's online customer service or call 0516-85871846 or 0516-85532705. Jiangsu Sifang Clean Energy Equipment Manufacturing's professional technicians will answer your questions in time.