Views: 1890 Author: Site Editor Publish Time: 2023-02-16 Origin: Site
Sifang Boiler adheres to the principle of technology as the core, market orientation and service as the purpose, and constantly speeds up technological innovation to enhance the core competitiveness of the enterprise. The comprehensive efficiency of leading products has been constantly improved, and they have won ministerial and provincial awards and customers' praise for their excellent performance, excellent quality and perfect after-sales service.
When installing the boiler dust removal equipment, it is necessary to follow the correct installation method and steps. Generally, the installation position should be determined before installation, and then the installation should be carried out according to the steps:
1. Installation of boiler dust collector bracket
After checking that the foundation meets the drawing and quality requirements, install the foundation bolt on the bracket, and then place the bracket on the basis of the marked datum line.
2. Installation of boiler dust collector
After the bracket is installed, lift the dust removal equipment and tighten the bolts connecting the dust remover and the bracket. During hoisting, it can be installed in sections or as a whole according to the situation (vertical or horizontal). The flange connected to the dust collector shall be tightly connected, and asbestos twisted rope shall be used as padding, and the padding shall be added to the inner side of the connecting bolt.
3. Installation of flue pipe of boiler dust collector
First install the smoke pipe and the diffuser of the dust collector from the outlet of the economizer or the outlet of the boiler rear smoke box. Asbestos rope shall be used as padding for flange connection between smoke pipes, and the connection shall be tight. After the smoke pipe is installed, check whether the position of the flange of the diffusion pipe and the inlet flange of the dust collector are appropriate. If it is slightly inappropriate, adjust the position and elevation of the dust collector bracket to make the dust collector and the smoke pipe connected properly.
4. Check the verticality and levelness of the dust collector
After the dust remover and smoke pipe are installed, check the verticality and water level of the dust remover and support. The perpendicularity and horizontal error of the dust collector is 1/1000, and then pour concrete into the anchor bolt hole. When the concrete strength reaches 75%, tighten the anchor bolt.
5. Install the air lock
The air lock is an important part of the dust collector and one of the key parts to ensure the effect of the dust removal equipment. Therefore, the connection of the air lock and the tongue plate should be tightly contacted, and the counterweight or hanging ring should be appropriate.
The above is Jiangsu Sifang Clean Energy Equipment Manufacturing's answer to this question. If you have any questions about other boiler related issues, please consult Jiangsu Sifang Clean Energy Equipment Manufacturing's online customer service or call 0516-85871846 or 0516-85532705. Jiangsu Sifang Clean Energy Equipment Manufacturing's professional technicians will answer your questions in time.